Bundle UNITS GPG 10 AND 12 SEERSlide 2
TECHNICAL SUPPORT 888-593-9988 MARK STOKES 713-861-2500 EXT. 630Slide 3
Model Number ChartSlide 4
SERIAL NUMBER 09 is for the month it was manufactured 0409456678 04 is for the year it was assembledSlide 5
12 & 10 SEER Packaged Gas Electric Fits in a standard size Pickup! 47" WideSlide 6
12 & 10 SEER Packaged Gas Electric Cooling Features: Convenient get to boards to the compressor High-effectiveness Scroll and Energy-productive responding compressor. Copper tube/aluminum blade loop. Fluid line channel drier. Completely charged R-22 framework. Louvered Guard ProtectionSlide 7
10 & 12 SEER Packaged Gas Electric Control Features: Convenient get to boards to the Evaporator curl and control area. Coordinate start framework, which incorporates a microchip based control for the whole start arrangement, all blower operation and all wellbeing circuits. Demonstrative Indicator accommodated investigating framework flaws.Slide 8
Design Objectives 2 – 5 ton Single Phase 3, 4 & 5 ton Three Phase 12 &10 SEER Cooling, 80% AFUE Heating Capable of extension to higher SEER evaluations Convertible Easy Access Service Panels Architectural GraySlide 9
12 & 10 SEER Packaged Gas Electric Heating Features: Convenient get to boards to the warming area. Excess gas valve, common gas and simple transformation to propane. Control helped ignition. L.P. Change Kit Available 12 & 10 SEER units offer a solid, T-140 Aluminized Steel tubular warmth exchanger. California Low Nox ApprovedSlide 10
Manufacturing stress including divider diminishing is minimized Wrinkles are set unequivocally where we need them Wrinkles elevate turbulence to help warm exchange and productivity Wrinkle-twist Process We start with T-140 Aluminized Steel tubesSlide 11
1-3/4" breadth fits inside a 1-1/4" width Tubes are joined with a restrictive procedure Velocity of ignition items is advanced Efficiency is boosted Dual-measurement/Muffler-joint We apply a protected procedure to join tubesSlide 12
1,000 ° F 300 ° F Tubular Technology Renders Clamshell Obsolete 800 ° F 1,000 ° F 300 ° F 300 ° F 300 ° F 110 ° F Non-uniform warm development Eyelets can pop Stress-breaks can shape Tube can develop long and distance across Growth is uniform at the cross-area No open door for stretch splitsSlide 13
CLEARENCE FROM COMBUSTIBLE MATERIALSSlide 15
CURB INSTALLATIONSlide 16
CONDENSATE DRAINSlide 19
FLUE HOOD & BUG SCREENSlide 20
12 & 10 SEER Packaged Gas Electric McDaniel Metals By AccessoriesSlide 21
10 & 12 SEER Packaged Gas Electric Blower Features: Convenient get to boards to the blower segment. Channel rack included on 12 SEER substantial (4 &5 ton) body. Simple evacuation of blower with two screws. Multi-speed evaporator blower. Completely protected with covers of fiberglass.Slide 22
12 & 10 SEER Packaged Gas Electric Base Features: 042 Aluminized Steel Bottom/Base Pan 2" High Base Rails Shipped with four boardsSlide 23
DUST COVER INSTALLATIONSlide 24
RECOMMENDED FILTER SIZESSlide 25
Electrical 208/230 Volt Power associations and 460 Volt accessible in 5 Ton Cool just model Single Phase and Three stage models accessible Maximum Over current Protection dictated by modelSlide 26
Wiring All wiring ought to be made as per the National Electrical Code. Wire sizes and over current security ought to be resolved from the unit nameplate ampacity. Wire sizes ought not be littler than prescribed by these two sources. All outside wiring must be inside endorsed weatherproof channel. The unit must be for all time grounded as per nearby codes.Slide 27
HIGH VOLTAGE WIRINGSlide 28
LOW VOLTAGE WIRINGSlide 29
CHECKING THE COMPRESSORSlide 30
CHECKING CONTACTORSlide 31
CHECKING CAPACITORSlide 32
COMPRESSOR NORMINCLATURESlide 33
COMPRESSOR DIAGONSTICSSlide 34
TESTING FOR GROUNDED COMPRESSORSlide 35
FLOW RATERSlide 36
HEATING SIDE OF GPGSlide 38
CHECKING GAS PRESSURE Manifold Outlet Gas Pressure Natural… . Min. 3.2" W.C., Max 3.8" W.C. Propane… .Min. 9.7" W.C., Max. 10.3" W.C.Slide 39
CHECKING BURNERSSlide 40
BURNER BOX REMOVALSlide 42
CHECKING BURNERSSlide 43
CHECKING LIMIT SWITCHSlide 44
Pressure Switch Check Meter on AC Voltage Setting ; between Quick Connect on Pressure Switch and Ground Prior to Operation check for open side of Pressure Switch (No Voltage Present) When Pressure Switch Closes 24 Volts ought to be available on N/O side Issue: Watch for switch skip on breezy days Issue: Watch for P.S. drop-out for low weightSlide 45
CHECKING PRESSURE SWITCHSlide 46
CHECKING PRESSURE SWITCHSlide 47
PRESSURE SWITCHSlide 48
INDUCED DRAFT BLOWERSlide 49
Understanding ECM MotorsSlide 50
Understanding ECM Motors What does ECM mean? How does the ECM function? Variable Speed versus Constant Volume. What is PWM How does the ECM sense static weight? Investigating ECM engines.Slide 51
BLOWER MOTOR & HOUSINGSlide 52
Electronic ControlsSlide 53
B18099-18 Control B18099-21 Has Green Diagnostic LED B18099-21 Cannot be utilized alone; must be utilized with B18099-22 Control B18099-21 Control is set up for 50Hz Operation and for use in Europe (CE Mark)Slide 54
Control Environment +80 to - 40 Degrees Celsius (+176 to - 40 F) 10% to 95% R.H. Non-Condensing 98 to 132VAC Line Voltage 18 to 30VAC Control Voltage Frequency - 60Hz UL & cUL ApprovedSlide 55
General Functions "W" Input On (Call for Heat) Checks to see weight switch open Turns on Inducer Pressure Switch Closes; 15 Second Pre-Purge Starts Sparking & Gas Valve Turns On for 7 Seconds Flame Sensed Anytime During Spark Gas Valve Stays On Blower Comes On following 30 Second Delay "W" Input Off (Call for Heat Satisfied) Gas Valve De-Energizes Immediately Inducer Remains on for 29 Second Post Purge Indoor Blower De-Energizes after Selected Blower Off DelaySlide 56
General Functions Continued.... Single Compressor Mode (Tab is not Broken) "Y" Input On (Call for Cooling) 3 Minute Anti-Short Cycle Timer from the time the compressor was keep going on. Cooling Speed Blower following a 7 second postponement "Y" Input Off (Call for Cool Satisfied) Cooling Speed Fan Off following 60 Second Delay Dual Compressor Mode (Tab is Broken) first Stage Compressor is Energized Externally "Y" Input On for second Stage Cooling following 7 Second Delay "Y" Input Off ; Cooling Speed Fan off following 60 Second DelaySlide 57
General Functions Continued.... "G" Input On (Call For Fan) Fan Immediately on Heat Speed "G" Input Off Fan Immediately Shuts Off If "Y" input Occurs During "G" Blower Switches to Cooling Speed If "W" Occurs During "G" Blower off when Heat Blower On Delay Begins Continuous Fan Operates while control is in Heat Mode Lockout Test/Speed-Up Bypasses Compressor Short-Cycle Timer If Shorted for Over 4 Minutes ; Control Ignores = Operates NormalSlide 58
Diagnostic Codes Steady On = Normal Operation in Standby 1 Flash = Lockout for Ignition Failure or Flame Dropouts 3 Trials for Ignition or 5 Flame Losses 2 Flashes = Pressure Switch Open with Inducer On 3 Flashes = Pressure Switch Stuck Closed with Inducer Off 4 Flashes = Limit Switch Open Heat Speed Blower and Inducer On Until Limit Closes Blower Runs through Off Delay; Inducer runs through 29 Second Post-Purge 5 Flashes = Flame Detected with Gas Valve Off Blower and Inducer Both On Until No Longer Sensed Control Locks out But Senses Limit and Flame Control is Reset By Removing Power or following 1 Hour Automatically 6 Flashes = Compressor Delayed for Short Cycle/Staging Timer Status Light Off = Board Hardware FaultSlide 59
Flame Sense Checking Digital Meter set for least uA Setting Meter in arrangement with Flame Sense Rod Wire Control must read at least .5uA amid fire detecting period Average current perusing is around 3-5uA. Control continually screens Flame amid warming operation Issue: Flame Sense Rod gets eroded ; Clean w/steel fleece Issue: Flame Rod not arranged in Flame CorrectlySlide 60
Ground Check Meter set to Ohms or Resistance Setting Place Meter from P1-6 or COM fast associate with case ground Reading ought to be close to Zero ohms Issue: COM Quick Connect Loose ; causes board resetting when blower begins Issue: Flame Sensing issues if despicable establishing in frameworkSlide 61
GPG TROUBLESHOOTING THEORY OF OPERATION Control of warming, cooling, and fan works because of a standard indoor regulator Direct start utilizing a chip to control timing, fire detecting, and start retries Monitoring of framework weight switch and breaking point switch Control of gas valve, indoor fan, and initiated draft engine in view of the indoor regulator request and status of security data sources Control of compressor contactor Diagnostic marker to give data on energy to the control and control statusSlide 62
GPG TROUBLESHOOTING Summary of Timing Functions (in seconds) 1. Warm speed delay on and off happen simply after fire has been detected and fundamental valve (MV) is invigorated Selectable with jumpers 3. Demonstrates timing when "Two Stage Comp" tab is severed, clock gets to be postponement on make 4. Shows timing when "Two Stage comp"tab is not severed, clock gets to be compressor bolt out between cycles(I.e. Least planning between compressor cycles) 5. Prepurge timing (not postpone on )Slide 63
GPG TROUBLESHOOTING Inputs Limit Switch –The restrain change is associated with control pins 4 and 5. The point of confinement switch is associated is e
To assess the execution of existing specially appointed structures composed and built particular ...
Best in class Shipping Technology. Computerized Package Processing System can deal with 9,500 .. ...
It would be ideal if you exhort your Director, Schools promptly in the event that you are not a ...
London Specialty School of Obstetrics and Gynecology. Quiet Safety. Pivot and ... OG, Classroom, ...
Initially utilized by the Red Hat Linux appropriation, it now is the bundle organization of deci ...
CLEC Care. Client Education. Bundle 2004 BellSouth Telecommunications, Inc. ... Nearby Platform ...
CLEC CARE. Client EDUCATION. Bundle. Line Loss. Notice. Report. 2 ... The consummation date mirr ...
26. The Portuguese Bullfight. Social Metaphors. social representations can be inferred for ... 2 ...
4) Demonstrate and clarify how five bits of parallel code functions. ... Parallel is a kind of n ...
Main BEDROOM. Room 2. STUDY. Open air. Extras. Bundle INCLUSIONS ... BED LINEN - BEDROOM 2. 2 x ...
Shipping a bundle with UPS is as simple as... 1. Login 2. ShipTo 3. Bundle Information 4. ... Fo ...
Detached houses. Planned into new development. How and where ... Lexington, rural group. Northam ...
Every bundle has no less than 10 distinctive movement sorts to browse e.g. the
Is the appearance and soundness of the scene of your property critical to you? ... City,St Zip. ...
Fly from New York, through London, to Edinburgh. Stay in a five-star inn at the base of ... Make ...
ADUs sited in back parcel territories on greater parts and/or carport transformations ... ADU Op ...
Obscure: Canada, US, Australia, Japan, NZ, Ireland, Norway, Poland, Switzerland ... Un-consolida ...
SABBATH SCHOOL ACTION UNITS. Sabbath School Action Units. What they are and how they work. ...
Useful Units. . Useful Units. . . . . . . Figure 1.1. Essential utilitarian units of a PC.. I/O. ...